The Science Behind It
- Great for neutralizing acid waste stream
- Works better in digestor with good mixing
- Recovery if an anaerobic system goes sour
- Safe to handle and safer for your system
Exact Dosing Bench Test
Running this simple titration test is the best way to accurately know how much to add.
1. Prepare Chemicals: Make a slurry mixture of 50g of Magnesium Hydroxide and 1000 mL of distilled water. Add the slurry to a bottle with a cover so it can be shaken up regularly.
2. Prepare Sample to Be Tested: Collect 500 mL of well mixed (if possible) anaerobic digester sample in a 1000 mL beaker. Place the beaker on a mixing plate with a magnetic stirrer or put in a 1000 mL beaker with mixing.
3. Add magnesium hydroxide until desired pH is Achieved: Test and record the initial pH, then add 5 mL portions of magnesium hydroxide. After each 5 mL magnesium hydroxide addition, mix the digester sample for 3 minutes and then test and record the pH and add another 5 mL until the pH is at 7. Magnesium Hydroxide should be shaken or mixed before each 5 mL addition.
4. Calculate Dose Required for Full Scale Treatment: Once the pH reaches 7, the dose of 5 mL equates to 210# of magnesium hydroxide per 100,000 gallons digester volume. This means you will need to add 210 pounds of Boost N Lock per 100,000 gallons digester volume or other solid pH adjuster for each 5 mL added to the beaker.