Nitrifying organisms to reseed nitrifying cultures
- Restores populations of nitrifying and nitrite reducing organisms
- Works great in water temperature as low as 39°F
- For use in aerobic wastewater systems
- Ships next day and guarantees full recovery in 6-10 days
- Dose rate & product info
*This product is only available for purchase by phone: 888-757-9577
$552.00 for a 2 gallon case (1 gal of each)
The Dynamic Duo makes use of the combination of our VitaStim Ammonia Assimilators and VitaStim Nitrifiers for premium ammonia removal. They contain high amounts of active nitrifying bacteria including Nitrosomonas, Nitrospira, Nitrobacter and heterotrophic nitrifiers at the highest concentration in the industry. They also contain powerful micronutrients to boost the growth and reproduction of the nitrifying bacteria. The combination of these two products produces the fastest nitrification recovery. The biostimulants and hetrotrophic cultures in VitaStim Ammonia Assimilators works with the VitaStim Nitrifiers concentrations to produce the highest and fastest growth rate. We use two types because they remove ammonia with two different mechanisms, in a certain sense, you can say one is like rear-wheel drive and the other front. The use of both propels your plant to ammonia removal and full nitrification.
The Dynamic Duo are specifically adapted to work in a range of wastewater conditions, taking into account the chemistry you currently use, any physical limitations of the plant, and the present microorganism population.
Nitrite Lock in Industrial Plants
Nitrite Lock is an issue where nitrite oxidizing bacteria are unable to keep up with nitrite production by ammonia oxidizing bacteria. This leads to an accumulation of nitrite which can result in inhibition of ammonia removal. This rarely is experienced in municipal systems but can often occur in industries with high levels of incoming ammonia. Supporting a strong population of nitrifying bacteria can help prevent conditions like this from arising. Click on the case studies tab to read about a hog slaughter facility that ran into this issue, and how they recovered.
Applications and Benefits
- Municipal wastewater
- Industrial wastewater
- Rendering facilities
- Rapid recovery from upset
- Improved nitrification
- Super concentrate formula
- Lower effluent ammonia
- Rapid start-up of new plants
- Creates healthier biomass
- Increases cell metabolism
A Virginia Beach wastewater authority operates a 50 MGD wastewater treatment plant, and from time to time their plant struggles with nitrification.
As you can see from the chart below, the addition of VitaStim Dymanic Duo turns the plant around fast.
Within 3 days the ammonia levels were in compliance. See Graph in New Window
Sugar Processing Plant
A sugar processing facility in Minnesota lost nitrification in its aerobic tanks. This facility has a 1 MGD flow rate, their basin is 2 MGD, and the ammonia level was at 189 ppm.
They ordered 9 gal of VitaStim Nitrifiers and 9 gal of VitaStim Ammonia Assimilators. Then added 4 gal of each product initially and then added 1 gal per day thereafter.
4 Days Later: The effluent ammonia had lowered to 17.2 ppm “It was like magic.” – Dr. David Rein, PhD, PE, Rein & Associates
Hog Slaughter Facility
This industry is a hog slaughter facility with two anaerobic lagoons followed by an activated sludge process with a large 1.8-million-gallon aeration tank with a 2-day hydraulic retention time (900,000 GPD flow). Wastewater entering the aeration tank contains low levels of BOD (30-40 ppm typically), but high ammonia levels (200 ppm incoming ammonia). Alkalinity in this system occasionally gets as low as 50 ppm, but usually is 120 ppm. Ammonia in the aeration effluent is typically below one ppm, with nitrite levels below detection limits. In early October, this plant experienced heavier than typical loading which led to a pH drop to 6. In addition, a mistake occurred in which a wasting pump was left on for 24 hours, leading to significant loss of solids. Initially ammonia spiked up to 5.86 ppm but returned to normal within a day without treatment. However, nitrite levels in the basin progressed to around 45 ppm before treatment occurred.
This facility added 2 gallons of Dynamic Duo initially, and after 1 day their nitrite levels to decrease to 7.7 ppm. A temperature shift occurred in the system the following night which led to the nitrite levels in the system increasing back to 32 ppm. As treatment continued, nitrite levels returned to 7.5 ppm after 1 more day of treatment recovered to 0.199 ppm nitrite in effluent after 3 more days.